Caterpillar generator sets are designed and manufactured to provide ease of installation and simplicity of operation. The correct rating selection and the correct installation of a generator set are crucial for a proper and smooth operation.
1) Indicative guidelines for designing the installation site/room of a generator set
The following brief instructions intend to assist and advise upon a generator set installation in order to ensure the best possible results for the user-owner*:
Proper ventilation of the installation site/room
For correct engine combustion and heat dissipation of the motor, plenty amount of air is required. All the specific information for the needed volume of fresh air of each genset model is included in its technical brochure.
Rising temperatures within the installation and operating site of a genset must not exceed 8° - 12°C above the ambient temperature.
Exhaust piping and silencer should be installed in a way that will allow sufficient space for service access to the maintenance technicians. Proper piping support is crucial to prevent vibration transmission to the generator set.
The entire exhaust system must be properly insulated to avoid heat dissipation/transfer to the installation room.
Finally, for the correct generator set operation, the back pressure of the entire exhaust system should be taken into account and must not exceed the recommended manufacturer limits.
Mounting of a generator set
For the proper generator set operation it is crucial to build a completely leveled base/foundation, thus offering adequate seating for the unit. The base/foundation should be of sufficient strength based on the weight of each specific generator set. A proper seating does not affect the critical engine-alternator alignment. A generator set installation on an unleveled surface can cause damages such as distortions of the engine block and torsional stress to the welding and engine foundation iron.
Ιn high-power generating sets (over 1000kVA), Caterpillar provides alternatively special anti-vibration equipment (rubber/spring), which is placed between the generator set and its installation surface (base/foundation) for further vibration isolation. A general rule is to place one pair of anti-vibration rubber/spring near the center of gravity of the generator set and the remaining pieces in equal distances in order to equally distribute the weight of the generator set.
In addition, adequate space around the generator set is necessary for its proper operation as well as for easy access of the service technicians during maintenance intervals (a distance of about 1 meter perimeter is quite satisfactory).
For correct connection of power generators, special attention should be given to the following*:
2) Indicative instructions/checks for uninterrupted operation of generator sets
Proper operation of generator sets
Proposed inspections during operation of generator sets
The following actions should be followed by the operator of a generator set in order for the genset to operate and perform at its full capacity*:
For the direct/auto-start of the generator set, its battery system should be always under load. For this purpose,
3) Engine fuel
The CATERPILLAR generating sets use diesel as an operational fuel. The quality of the diesel fuel used affects the engine performance.
Also, the fuel level within the tank is important to be at a lower point than the combustion system (burner, oil pump, etc) to avoid the pressurizing the whole fuel system.
Important disclaimer on biodiesel (regarding the biodiesel fuel)
Dear Clients and Partners,
Lately, popular discussions are a fact in what regards to the quality of the available diesel on the domestic market (according to European standard EN 590) and several problems are attributed to it, especially in internal combustion engines. In general, biofuels are promoted by the European Commission, in an effort to limit emissions to the atmosphere:
The Disadvantages of using biodiesel are:
Additionally, storage of biodiesel at large intervals generates fungi that grow and cause fungal mud which affects negatively the fuel circuit causing operational problems. This is a frequent occurrence on generator sets used as back-up (stand-by) or seasonal solution and the reason is because the biodiesel is stored for long periods.
This precipitate is deposited on several parts, for example on the oil pump and the bottom and the sides of the tank, resulting in pump’s malfunction and problematic operation due to tank’s deterioration, which if not cleaned / replaced will affect any remaining diesel left in it, even if this is renewed.
Eltrak – Caterpillar, always close to its customers, proposes the following preventive actions/steps in order to protect the customer and his investment:
Letter / Research from T.E.E. Dr Mechanical Engineer Leonidas Ntziachristos, <<The use and the impacts of biofuels in combustion engines>> («Χρήση και επιπτώσεις των βιοκαυσίμων σε κινητήρες εσωτερικής καύσης»):
* The purpose of these general installation and operation instructions are only to advice and inform and in no way contain 100% of a complete genset installation instruction set.
The Caterpillar offers the widest range of generator sets starting from the 13,5kVA (10,8kW) reaching and 17.550kVA (14.040kW) covering the most demanding needs for power. Caterpillar gensets are the only ones in the market that combine a generator and the engine from the same manufacturer (Caterpillar).
Diesel generating sets of Caterpillar, suitable for backup applications (STANDBY) and DC (PRIME) function is three-phase or single-phase, water-cooled, low, automatic or manual operation, open or closed type (soundproofed), low speed (max 1500rpm), with built-in fuel tanks.
Besides generator sets that have the basic (standard) built, Caterpillar provides solutions for each specific requirement, like gensets in parallel (GenSets of the same or different ratings), remote refrigerators, remote monitoring capabilities, etc.
In this website you can find most of the generator sets available from Caterpillar's product line, with detailed technical information on each unit. Choose the item that you are interested in to access detail information from the manufacturer.
Caterpillar's gas generator sets are made to run on your most abundant gas sources with fuel flexible options. Caterpillar generator sets have been engineered for high efficiency, low life cycle costs and to meet global emissions specifications. Ranging from 20 to 9700 ekW, with customizable options to match your power needs, Caterpillar's gas generator sets are easy to select, permit and install. Power the possibilities of your world with world-class power. Tailored designs for natural gas, biogas, coal gas, and alternative fuels. New engine technologies deliver power, heat, or cogeneration with world class electrical and thermally efficiency. Factory-sourced containers, heat recovery modules, and control systems. Optimized for operation in parallel or disconnected from a primary electric utility.
|CHP for Greenhouses|
|Many industrial facilities and commercial facilities can reduce operating costs by implementing a Cat® CHP system (also known as cogeneration) using clean pipeline natural gas as a fuel source||Cat® Generators help make greenhouses better
with power built to cut costs and boost plant health
|Agricultural biogas cogeneration||Landfill gas cogeneration|
|Power your agriculture operations with
generators built to run on fuel you already
produce-fuel with byproduct gases.
|Cat® generators are making landfill power an
efficient and environmental operation-with systems
that run entirely on waste gas
CAT 50 Hz CONTINUOUS – GAS RATINGS, 68 – 14040 ekW
*All ratings at 0.8 pf. DF: Dual Fuel.
1Further gas qualities on request
Tel: Athens +30 2108196969
Fax: Athens +30210 8078668
Service Marine & Industrial engines & Generators
Tel: +30 210 8196900, +30 2310 014442
Fax: +30 210 8079174, +30 2310 754606